KVVP shielding control cable is suitable for the connection of control and monitoring circuit of rated cable 450/750V or below, mainly to prevent electromagnetic interference.
It is suitable for connection lines of control, monitoring circuit and protection circuit with rated voltage U0/U 450/750V or below. It is mainly used in places where electromagnetic interference is prevented and shielding is needed.
Conditions of use
The long-term permissible working temperature of cable conductor is 70 C, and the high-temperature shielded cable can reach up to 300 degrees.
Cable laying and installation allowable bending radius:
1. Unarmoured cables should be no less than 6 times the outer diameter of cables.
2. Cables with armoured or copper band shielding structure shall be no less than 12 times the outer diameter of the cable.
3. Soft cable with shielding layer structure should be no less than 6 times of cable outer diameter.
Scope of use
1. Polyethylene Insulated PVC Sheathed Shielding Control Cable
Scope of Model Name Use
KVVP copper core PVC insulation and sheath braided shielding control cables are laid in indoor, cable trench, pipeline and other fixed occasions requiring shielding.
KVVRP Copper Core PVC Insulation and Sheath Braiding Shielding Control Soft Cable Laying in Indoor Mobility Requirements Soft, Shielding and other occasions
KVVP2 copper core PVC insulation and sheathed copper strip shielding control cables are laid in indoor, cable trench, pipeline and other fixed occasions requiring shielding.
KVVP3 copper core polyvinyl chloride insulation and sheath aluminum-plastic composite belt shielding control cable laying in indoor, cable trench, pipeline and other fixed occasions requiring shielding
KVVP2-22 copper core PVC insulation and sheathed steel belt armoured control cables are laid in indoor, cable trench, pipeline, directly buried and other fixed occasions which can withstand large mechanical external forces.